ANSI/TIA/EIAA Approved: May 16, TIA/EIAA. Administration Standard for. Commercial Telecommunications. Infrastructure. TIA/ EIAA. This guide is intended to be used as a reference to the application of the. ANSI/ TIA/EIA A Standard. It in no way reflects all the necessary infor-. ANSI/TIA/EIA Administration Standard for the. Telecommunications Infrastructure of. Commercial Buildings. Distributed by NDS INFORMATION- TELECOM.
|Published (Last):||5 March 2008|
|PDF File Size:||16.57 Mb|
|ePub File Size:||11.89 Mb|
|Price:||Free* [*Free Regsitration Required]|
The following is the color coding scheme recommended in B: Requirements For Labels All labels must use a permanent identifier that can be easily ti — that is, a useful numbering scheme.
structured cabling test Chapters 9,10,11,12,13 Flashcards Preview
The labeling principles that underlie B include the following: The labeling system, and the identifiers used, must be agreed upon by all stakeholders. PVBX, LANs, and individual computers Yellow — Auxiliary circuits, such as alarms and security systems Red — Key telephone systems termination Record Keeping Requirements Drawings and documents must be secured and backed up by the building administration.
While recommended, color coding is not required, and compliant coding may be accomplished using color labels or color bands.
Labeling should be pervasive; cables and connecting hardware should be labeled, but so should iea and firestops, grounding and bonding locations, racks, cabinets, ports, and telecommunications spaces. All jack, connector, and block hardware may be labeled on either the outlet or panel. The following is a simple example of a cable identifier.
All labels must match up with the permanent record.
A04 — As before, the first element identifies the cabinet location, but this time for the far end of the cable. Any moves, adds, and changes MACs must be documented with a change order.
ANSI TIA EIA – A Guide – English – Brady Europe
This is port This particular cable would have a corresponding 606aa on the other end the data center end, in this case which would read: Permanent records must cross-reference all identifier information. Labeling must be logical and consistent, across all locations, matching the project drawings.
These principles are then translated into specific requirements. Labels for station connections may appear on the face plate.
Labeling must be easily read, durable, and capable of surviving for the life of the component that was labeled.
Each cable and each pathway must be labeled on each end, and each label should identify the termination points of both ends of the cable. This scheme must be logical in its organization, using alphanumeric characters for ease of reference.
This particular cable would have a corresponding label on the other end the data center end, in this case which would ea. It identifies the termination point for both ends of the cable, with the near end shown first.
ANSI TIA EIA – 606A Guide – English
All labels must meet requirements for legibility, defacement, and adhesion, specified in UL The following is the color coding scheme recommended in B:.
Wire Color Coding While recommended, color coding is not required, and compliant coding may be accomplished using color labels or color bands. The labeling scheme must identify the associated physical locations building, room, cabinet, rack, port, etc.
MACs must be recorded and updated in the permanent records.