manual, RUN/STOP, and alarms) and the PV or SV. E5CN/E5AN/E5EN/E5GN Digital Temperature Controllers User’s Manual Basic Type E5CN-R2MT E5CN/E5AN/E5EN Digital Temperature Controllers User’s Manual Basic E5CN -R2MT AC or E5CN-R2MTD AC/DC24). E5CN/E5CN-U Temperature Controller User’s Manual (Cat. No. H). E5CN Temperature Controller Communications User’s Manual (Cat. E5CN-R2MT-
|Published (Last):||3 November 2016|
|PDF File Size:||15.1 Mb|
|ePub File Size:||19.42 Mb|
|Price:||Free* [*Free Regsitration Required]|
Know and observe all prohibitions of use applicable to this product. Easily see the status from e5cn-r2mt-5500 distance with PV display with threecolor switching function. Pt or JPt No models with analog inputs Improved models 7.
Back-connecting Socket P3GA 27 dia. Group mounting is not possible in the vertical direction. A password is required to enter the advance function setting level and the calibration level.
Use the Temperature Controller within a power supply voltage and load that meet all specifications and ratings. Equivalent to IP50, rear case: Model selection is simplified, stocks are reduced, and fewer maintenance parts are required.
Option Units cannot be used for Plug-in models.
OMRON E5CN Datasheet: Ordering Information
Refer to Precautions on page It cannot be removed with the E5CN-U. SSR failure detection alarm setting range 0.
C al1l Lower-limit 1 alarm value 0 a 40 a ct1 Heater current value 1 0. Locations subject to severe temperature changes? Allow at least 30 minutes for the Temperature Controller to warm up. H Press the Level Key for at least 3 s. Push the adapter along the Controller body from the terminals up to the panel, and fasten it temporarily. When two or more Temperature E5cn-r2jt-500 are mounted horizontally close to each other or vertically next to one s5cn-r2mt-500, the internal temperature will increase due to heat radiated by the Temperature Controllers and the service life will decrease.
The previous ThermoTools cannot be used with the new Controller models.
You can move only to the operation level by operating the keys on the front panel from the manual control level. Panel interior dimensions for panel mounting? Use crimp terminals with the specified dimensions M3.
Locations subject to exposure to water or oil? Doing so may occasionally manal in minor electric shock, fire, or damage to equipment. Outputs will turn OFF depending on the mode when switching to the initial setting mode.
EUROTHERM ERO LFS Controller PID Heater Break Alarm Rs W/ Manual Hardware | eBay
E5CN Mounting to a Panel 1. Due consideration must be given to this time when incorporating Temperature Controllers in a sequence circuit. Do manua, use thinner or other solvent-based substances. Using any other sockets will adversely affect accuracy. DC loads cannot be connected. Tighten the terminal screws using a torque between 0. Connect to either a thermocouple or platinum resistance thermometer with the same model.
Protect Level Press the Level Key for at least 1 s. The input type setting numbers have changed to allow for multiinput specifications.
To convert grams into ounces, multiply by 0. Voltage outputs can be used for both heating and cooling for Models with Two Control Outputs. Be sure to refer to the following user manuals for application precautions and other information required for operation before attempting to use the product. SP used by multi-SP Protect Level The time taken to move to the protect level can be adjusted by changing the “Move to protect level time” setting.
Pt or JPt Infrared temperature sensor: Fire may occasionally occur if terminal screws become loose.
Recommended panel thickness is 1 to 5 mm. Set the alarm types for alarms 1 to 3 independently in the initial setting level.
When placing manuual Controller back in the case, make sure that electronic parts do not come in contact with the case. Easy setting with segment displays. Do not block the ventilating holes. Press the Level Key less than 1 s. Output when an input error output is enabled in the Advance Function Setting Level.