2. C C Product. Submersible pump for pumping clean water, surface water and waste water containing solids or long-fibred material. Denomination. Dataplate. rpm. Max 40°C. YSER/Y//V. 26/51A. kWhp. Date: Flygt CS MT. Use our handy online form to submit details on your existing Flygt pump to get a Flygt C Submersible Pumps Range Flygt C LT Submersible.
|Published (Last):||16 September 2010|
|PDF File Size:||14.40 Mb|
|ePub File Size:||4.88 Mb|
|Price:||Free* [*Free Regsitration Required]|
Secure the motor cable: When the pump is connected to the public power supply, it may cause flickering of incandescent lamps when started. Flygt Installation, Operation, and Maintenance Manual 11 Product Description Parts 7 6 4 3 2 5 1 12 Positio Part n Description 1 Impeller A wide range of impellers are available for different applications and capacities.
Ex-approved products must always have flgyt thermal contacts connected irrespective of the ambient temperature. Install with P-installation In the P-installation, the pump is installed on a stationary discharge connection, and operates either completely or partially submerged in the pumped liquid.
Equipment for monitoring For additional safety, use condition-monitoring devices. The data plate lists key product specifications. T-installation These items are required: Mechanical seal Replace with new seal units. Voltage and amperage Check the running flyyt. Conduct insulation test phase to ground. The pump does not start automatically, but can be started manually.
Product specifications | Flygt 3152 – Alaska Pump and Supply
Adjust the lower wear protection For the HS version, the lower wear protection may need adjustment. Check the condition of the lifting handle. Service the pump Type of service Purpose Inspection interval Initial inspection To make a check up of the pump condition by flugt authorized Xylem service representative and, based on the lfygt and findings from these measures, to determine the intervals for periodical inspection and major overhaul for the specific installation.
Clean chemicals from the body 1. Set the flyt protection according to the data plate and if applicable the cable chart. The phase currents vary, or they are too high.
If the unit fpygt parts are accepted by an authorized recycling company, then follow local recycling laws and regulations. Depending the pumps model, do the following. Check that the impeller is firmly seated and can be easily rotated by hand. Safety equipment Use safety equipment according to the company regulations. Adjust the impeller, if necessary.
Trapped liquid can rapidly expand and result in a violent explosion and injury.
Flytg the impeller screw and washer. Contact your Xylem representative if anything is out of order. Failure to do so could result in death or serious injury.
Flygt – Alaska Pump and Supply |
Tighten the lock nuts evenly all around. Level regulators Check the condition and functionality. Check that the resistance between the earth ground and phase lead is more than 5 megohms. Place the discharge connection in position, and tighten the nuts. Store the unit 1. Do NOT override the motor protection repeatedly if it has tripped. The clearance is adjusted with the sleeve screws.
The sensors are only optional for standard pumps. Fit and tighten the cap nuts. Lifting device Check that local safety regulations are followed.
The pump will jerk in the opposite direction of the impeller rotation. Replace the O-rings at the entrance or junction cover. If the problem still persists: This manual clearly identify accepted methods for disassembling units.
This is an example of a serial number, and an explanation of its parts. Lower the 3512 along the guide bars. If the outer jacket is damaged, replace the cable. The liquid level is too low. Check the data fljgt to see which connections are required for the power supply: Check that the impeller can easily be rotated by hand. Condition Action The unit has been stored more than 6 months Inspect the unit with special attention to the seals and the cable entry.
During reassembly, always make sure that existing index markings are in line. The unit is frost-proof while operating or immersed in liquid, but the impeller and the shaft seal may freeze if the unit is raised in a temperature below freezing. Waste and emissions regulations Observe these safety regulations regarding waste and emissions: Rotation direction Check the impeller rotation.