Buy IEC Ed. Instrument transformers Part 6: Requirements for protective current transformers for transient performance from SAI. Accuracy classes for transient cores according to IEC Error limits for TPX, TPY and TPZ current transformers. Error limits for TPS. IEC Additional requirements for current transformers. IEC IEC IEC Additional requirements for inductive.
|Published (Last):||27 November 2007|
|PDF File Size:||3.43 Mb|
|ePub File Size:||19.55 Mb|
|Price:||Free* [*Free Regsitration Required]|
Partial discharge analysis on instrument transformers. Page 46 – Example on how to connect a star connect Don’t have an account?
If you need to be able to add standards to the monitoring service, you must register as a user with your own username and password. Feeder protection and control feeder protection 79 pages.
IEC System of Conformity Assessment Schemes
Top Blog at WordPress. The new and old standards are essentially identical, but IEC consolidated two parts of the older standard:. Table of Contents Add to my manuals 600446. Instrument transformers — Part 6: Page 78 – Setting guidelines Page 79 Page 80 – Meshed network with parallel line Page 81 Page 82 – Directional phase 600446 protection Comments 0 Trackbacks 0 Leave a comment Trackback.
Page 56 – Examples how to connect, configure and s Page – Evolving fault Page – Automatic continuation of the auto reclo A web subscription provides an easy and secure access to standards, and you are guaranteed to always have the latest edition.
Instrument transformer testing – OMICRON
Please upgrade your browser or use another browser to view this page correctly. Hence, it is essential to inspect and calibrate those instrument transformers at regular intervals.
6044-6 A corresponding rated equivalent limiting secondary e. You are commenting using your Twitter account. The moment new editions of the standards you monitor are released, changes are made, or appendixes are published, you will be alerted by email.
Page – Switch onto fault logic Page Page Page – Four step directional negative phase seq Page Page Page – Two step residual overvoltage protection Instrument transformer testing Instrument transformers for metering purposes must have a high degree of accuracy up to class 0.
Leave a Reply Cancel reply Enter your comment here Get your local contact Find contact. Contact us News 6004-6 Legal Imprint.
Notify me of new comments via email. Monitoring Standards monitoring is a free service designed for you who wish to be alerted of changes to or new editions of the standards required in your work.
EVS-EN – Estonian Centre for Standardisation
Page 54 Page 55 – Rated primary current and minimum pickup Comments to this Manuals Your Name. Send us an Email Send mail. Instrument transformers for metering purposes must have a high degree of accuracy up to class 0. Instrument transformers for protection purposes supply protection relays ifc must also function accurately at a multiple of the nominal current. Page – Reactors and transformersEquipment prote Page – External selection of auto reclosing mod The website specified the CTs were 0.